Two sets of Mars 100 unit are installed in the basement of the famous bimodal tower in Kuala Lumpur, the capital of Malaysia. Each unit can generate 18.2t/h, 28 bar steam while generating 11000 kW. With the centrifugal refrigerator driven by steam turbine, it can generate 5000RT cold water.
A Taurus-60 generator set with low NOx emission was installed at Duquesne University in Pittsburgh, Pennsylvania, USA in November 1997. Duquesne University, in consideration of the energy conservation and environmental protection of the University, jointly invested with equitable Energy Co., Ltd. to build this cogeneration system. Duquesne University once used 30 large mechanical air conditioning and refrigeration devices, which are evenly distributed throughout the campus. The power is provided by the local power grid, the electric centrifugal chiller is distributed in the building to provide cold water, and 4 boilers provide steam in a centralized way. On the one hand, this old way of energy supply is inefficient, on the other hand, it pollutes the environment. The purpose of this project is to simplify such a large refrigeration unit, chiller and other equipment groups, enhance the ability of campus energy supply unit to provide unified heating, cooling and steam, fully recycle the
Al Karam textile mill is a key processing enterprise in Pakistan and a major exporter of cloth raw materials. Among them, the joint factory in Karachi also operates spinning, weaving, finishing, processing, printing and dyeing equipment. The electric load demand of textile mill is 6.5mw electric power and 15t / HR steam respectively. The plant first bought electricity from the State Grid, and later, considering the reliability of the grid system, it added a standby gas engine. In 1992, the textile factory decided to adopt the gas turbine generator set with triple supply, which can provide the power and steam in the field reliably and stably, and save the energy cost in the factory to the greatest extent. The project adopts a half horse 50 generator set (double motor), which can provide 11kv and 6MW power at 32 ℃. The exhaust gas discharged by the gas turbine enters into the waste heat boiler and can generate steam with a pressure of 15barg and 15t/h for use in the textile process. The
The first phase of Pudong Airport adopts the energy supply mode of "large concentration and small dispersion". In the power facility area of the airport, a central cooling and heating main station energy center is built, which is mainly responsible for supplying cooling and heating to the terminal, comprehensive office area, aviation food catering area, freight area, flight support area and business facility area, among which the base area and maintenance area of the airline company, etc. Single independent refrigeration and heating scheme is adopted. The energy center adopts the centaur-50, dual fuel (natural gas / diesel) gas turbine generator set, which can provide 10.5kv, 4000kW power; 9barg, 11t/h steam. The turnkey project was completed in 1999 and put into use in 2000. At the end of 2004, considering the decrease of natural gas supply pressure, a natural gas booster station (Shanghai Mariso Turbomachine Service Co., Ltd.) was added, which has been running well since January 2005
In December 1996, eastern energy and catamount Energy Co., Ltd. jointly invested and operated a set of steam turbine auxiliary Cogeneration Equipment including two Mars 100 gas turbines.(STAC), which provides power to two food plants (Magic Valley and magic West food) located in south central Idaho, more than 100 kilometers away. Waste heat boiler converts flue gas into steam, which is used to drive cutting machine, washing machine and dryer. The remaining steam drives the turbine to generate electricity. The power output of each food factory is 820000000kw. In Rupert, the average steam output is 13600kg / h; in Glenns ferry, the average output is 9070kg/h.
Sichenia ceramic factory, Italy, obtains ceramic slurry raw materials from Modena, mainly produces floor tiles, refractory bricks, bathroom fixtures and other products. In order to reduce the energy cost of the plant, a 1.1mw Saturn 20 gas turbine was installed. The power generation of the unit is incorporated into the power grid of the ceramic plant, and the flue gas directly enters the heating device to dry the ceramic products.